The following Plishner weekend update was provided by Steve Plock.
Strong winds and high humidity conditions created a pretty chilly and challenging work day for Ed Corn and Steve Plock at the Plishner site this past Saturday, May 14. Thanks to Skip MacCaulay from Lacombe, Alberta for his donation of a DC-to-AC inverter that Ed installed as the primary, along with another inverter donated by Ray that Ed installed as a backup.
An Anderson Power Pole distribution unit was also installed in the communications trailer. Light fixture attachment points were installed in the upper pedestal so that future lighting can be installed. The voltage regulator circuit board for the propane generator was remoted to the North wall of the generator shed and the connecting wires were placed in conduit. Hopefully, this placement will eliminate or reduce the heat build-up and vibration at the regulator board compared to when it was mounted on the generator.
A hole was cut in the plywood of the eastern (bunker) end of the generator shed and a louver panel installed. There is now a substantial air flow created inside the shed with the louvers open and the generator door closed. Generator oil was changed on a prior visit and the 1000 gallon propane tank is now at 30%. The tank main shut off/on valve will be repaired before adding more propane to the tank.
Thanks to Ed Corn and Steve Plock for their time spent at the Plishner site this past weekend.